Action / Decisions Pending / Follow up
<! 2. Drawings illustrating duct coordination at elevators 5 and 6 were>
A&P confirmed coordination.
<! 3. JV team requested verification that air intake shaft at>
A&P confirmed duct location per sketch.
<! 4. JV team requested confirmation that the sketches provided by KHA>
Although concept was approved, A&P requested copies of sketch for final review.
Confirmation from A&P by 11/13/98.
<! 5. Is plumbing shaft required for janitors closet plumbing?>
A&P advised: 6" stud wall capable of housing plumbing. No shaft required
<! 6. JV team requested information about elevator machine room HVAC>
A&P to review drawings included in 50% documents and advise of necessary
<! 7. PB presented sections and plans at elevator 7 and 8 with adjacent>
AA presented drawing showing revised
duct layout in this area.
Plots of revisions to be issued to JV team
<! 8. CC requested section clarify fire dampers and access to them through>
KHA to provide sections with added
information. A&P to review.
<! 9. JV team requested revisions to elevator exhaust locations so exhaust>
A&P to study potential locations for duct through roof penetrations. A&P and JV
team to coordinate
<! 10 JV team outlined revisions required in basement due to structural>
JV team provided revised basement plan. A&P to relocate ducts and minimize
penetrations through shear wall.
<! 11 MF requested confirmation that the grease ducts as currently designed>
<! 12. Fresh air intake shaft extending into basement was discussed. >
11/13/98: JV team cut section and verified duct/structure clearance.
<! 13. Floor space for the basement fresh air intake air handling unit is>
JV team to revise area by adding
required walls around AHU.
<! 14. At grid line B, a shaft through all floors, extending to roof >
JV team to add shaft to plans.
<! 15. A&P documents call out where beam penetrations are required.>
A&P and SDE to coordinate beam penetrations.
<! 16. A&P requested structural support for 8" water line that extends into>
JV team and SDE to coordinate.
<! 17. A&P advised JV team that head clearance under plate girders between >
JV verified: the worst condition is actually 7'-5" at grid lines 2.6 and
<! 18. JB must have utility inverts to complete drawings.>
JV team has requested this information
from MCEP. It has not been provided.
<! 19. JB requested louver information.>
Louvers are water tight, no drains required adjacent to louvers.
<! 20. A&P requested deadline clarification. The next printing will>
Drawings dates and titles to be provided closer to printing time.
<! 21 A&P completed consultant composite plans. All disciplines were>
JV team to plot color composites for coordination purposes.
Copies will be provided for al consultants
<! 22. Telecom conduits need to be coordinated with A&P drawings.>
KHA to lead coordination effort
<! 23. Fire damper access: JM confirmed access provided through moveable>
A&P will review access to dampers in 50% set.
<! 24. A&P was advised by JV team that concrete curbs will extend around the>
Curbs do not currently appear on plans,
but will be added for reference.
<! Remaining Issues Still Pending >
<! 2. A&P asked about Laundry Equipment information. CC to ask Tim Comey to>
11/12/98: Options for exhausting discussed. JV team directed A&P to add
exhaust fan and assume exhausting from building under bay window soffit.
<! 3. Gas vault information was transmitted to KH. Vertical ventilation>
Resolution pending Clonia Cautis study.
<! 4. Louvers on the south end elevations were discussed. A&P advised that>
This proposal was not incorporated.
Exterior louvers were revised per Peter
A&P confirmed that revised louvers can
work if fan sizes are increased.
JV team directed A&P to increase fan
<! 5. JV team (KHA) and A&P to coordinate all fire damper locations and>
JV team will verify if damper locations conflict with elevator machine
room. Elevator shafts, etc.
<! 6. CC requested section through ceiling/floor assembly for verification>
A&P provided section. Floor boxes to be added to section.
<! 7. JV team (SH) gave A&P a copy of the louver study showing inadequacy of>
JV team (SH) to schedule additional time with A&P for resolution of
Meeting occurred 9/26: duct revisions in
basement resolved problems.
<! 8. Emergency generator exhaust currently conflicts with stair,>
JV team requested clarification of
exhaust requirements (distance/height
JV team to study options of not
extending exhaust to roof.
<! 9. A&P and JV team must coordinate venting of elevator shafts. Current>
JV team to study and coordinate with A&P.
<! 10 JB requested structural and JV team approval of the sump locations.>
JV team reviewed and approved layouts.
Files sent to FBA.
Sump locations must be modified
slightly. See Structural foundation plan
for conflicts: S2.01.
<! 11 Has confirmation been received by SF Thermal on steam vault?>
SF Thermal has not provided a review.